"<p><strong>SHEET VINYL FLOORING<\/strong><\/p>\r\n<p>The sheet vinyl flooring sampled from the bathroom has tested positive for 60% Chrysotile asbestos. During our<br>inspection, the flooring remained in good condition and does not pose an increased risk to workers or occupants<br>until disruption occurs.<br>WorkSafe BC High-risk procedures are to be followed during the removal of both the asbestos paper backing and<br>the vinyl wear surface. If more homogenous flooring is uncovered, or there is flooring found that was not referenced<br>in this report, these materials are to be included in the abatement or tested to determine composition before they<br>are handled. Daily air monitoring is required by a third-party company during high-risk abatement work, and air<br>clearance must be issued before regular access to the area is permitted.<\/p>"