"<p><strong>DRYWALL<\/strong><\/p>\r\n<p><\/p>\r\n<p>The drywall joint compound sampled from bath 1, bath 2, and the powder room has tested positive for 1% Chrysotile asbestos. At the time of our survey, the drywall was observed to be in good condition. Until the disruption or puncturing of this material occurs, there is no enhanced risk of exposure to workers or occupants.\u00a0<\/p>\r\n<p>WorkSafe BC Enhanced-Moderate to High-Risk work procedures must be followed for the safe and controlled\u00a0removal of asbestos-containing drywall. Due to the increased risk of exposure presented while removing overhead\u00a0materials, higher precautions are encouraged during the dismantling of drywall ceilings. A qualified third-party\u00a0company must provide daily air monitoring throughout any high-risk removal activities. An air clearance test that<br>achieves satisfactory results must be completed before risk procedures are downgraded, or regular access to the\u00a0work area is permitted.<\/p>"